;------------------------------------------------------------------------------
; This GSD (General Station Description) is provided by PI C3PG7 "PA Profile".
; This GSD is available for download at PI web server.
; The Profile GSDs cover the common subset of functions of devices of
; a specific PA device type providing interchangeability.
;
; This file describes the device type:
; Electro-pneumatic Actuator
; with 1 Actuator output
; Physical layer MBP.
; This file becomes valid with the PA profile version 4.0.
;
; Last modification: 2017-10-20
;------------------------------------------------------------------------------
#Profibus_DP
;Standard definitions, valid for all device types with MBP
GSD_Revision = 5
Vendor_Name = "Profile Process Control Devices"
Revision = "PA 4.x"
Protocol_Ident = 0
Station_Type = 0
FMS_supp = 0
Hardware_Release = "-"
Software_Release = "-"
31.25_supp = 1
45.45_supp = 1
93.75_supp = 1
187.5_supp = 1 ;needed to support spec. network devices
500_supp = 1 ;needed to support spec. network devices
1.5M_supp = 1 ;needed to support spec. network devices
3M_supp = 1 ;needed to support spec. network devices
6M_supp = 1 ;needed to support spec. network devices
12M_supp = 1 ;needed to support spec. network devices
MaxTsdr_31.25 = 100
MaxTsdr_45.45 = 250 ;exception for spec. network devices
MaxTsdr_93.75 = 1000
MaxTsdr_187.5 = 60
MaxTsdr_500 = 100
MaxTsdr_1.5M = 150
MaxTsdr_3M = 250
MaxTsdr_6M = 450
MaxTsdr_12M = 800
Redundancy = 0
Repeater_Ctrl_Sig = 0
24V_Pins = 0
Freeze_Mode_supp = 0
Sync_Mode_supp = 0
Set_Slave_Add_supp = 1
Min_Slave_Intervall = 250
Modular_Station = 1
Slave_Family = 12@Profile4
;end of standard definitions
;Device type specific definitions
Model_Name = "Electro-pneum. actuator (PhyL 1)"
Ident_Number = 0xB341
Bitmap_Device = "PA_B341n"
Max_Module = 1
Max_Input_Len = 10 ;READBACK(5), POS_D(2), CHECK_BACK(3)
Max_Output_Len = 5 ;SP
Max_Data_Len = 15
Max_Diag_Data_Len = 38
Modul_Offset = 1
Max_User_Prm_Data_Len = 16
Ext_User_Prm_Data_Const(0) = 0x80 ;DPV1 Status 1
Ext_User_Prm_Data_Const(1) = 0x00 ;DPV1 Status 2
Ext_User_Prm_Data_Const(2) = 0x08 ;DPV1 Status 3
;--- Startup parameter of the Physical Block (Slot 0)
;PrmText = 1 ;STARTUP_PARAM_VALIDITY
;Text(0) = "Ignored"
;Text(1) = "Applied"
;EndPrmText
;ExtUserPrmData = 1 "Startup parameters"
;Unsigned8 0 0-1
;Prm_Text_Ref = 1
;EndExtUserPrmData
;Ext_User_Prm_Data_Const(3) = 5,66,0,0,0x00
;Ext_User_Prm_Data_Ref(7) = 1 ;STARTUP_PARAM_VALIDITY (Unsigned8)
Prm_Block_Structure_supp = 1
PrmCmd_supp = 1 ;slave supports PrmCmd
Slave_Max_Switch_Over_Time = 20 ;=200 ms
Slave_Redundancy_supp = 1 ;slave is not redundant but can be connected to a flying master
Info_Text = "Electro-pneumatic actuator with PROFIBUS PA (MBP) \
communication interface."
Ident_Maintenance_supp = 1
;----------- Description of extended DP features: ---------------------
;
DPV1_Slave = 1
C1_Read_Write_supp = 1
C1_Max_Data_Len = 128
C1_Response_Timeout = 1000
C2_Read_Write_supp = 1
C2_Max_Data_Len = 128
C2_Max_Count_Channels = 1
Max_Initiate_PDU_Length = 52
C2_Response_Timeout = 1000
DPV1_Data_Types = 0
WD_Base_1ms_supp = 0
Check_Cfg_Mode = 0
;----------- Description of device related diagnosis: ---------------------
;
Unit_Diag_Bit(16) = "Status appears"
Unit_Diag_Bit(17) = "Status disappears"
Unit_Diag_Bit(35) = "Restart" ;DIA_WARMSTART
Unit_Diag_Bit(36) = "Application reset" ;DIA_COLDSTART
Unit_Diag_Bit(37) = "Maintenance required" ;DIA_MAINTENANCE
Unit_Diag_Bit(40) = "Maintenance alarm" ;DIA_MAINTENANCE_ALARM
Unit_Diag_Bit(41) = "Maintenance demanded" ;DIA_MAINTENANCE_DEMANDED
Unit_Diag_Bit(42) = "Function check" ;DIA_FUNCTION_CHECK
Unit_Diag_Bit(43) = "Out of specification" ;DIA_OUT_OF_SPEC
Unit_Diag_Bit(44) = "Parameter update" ;DIA_UPDATE_EVENT
Unit_Diag_Bit(55) = "Extension available"
;NE107_COMMON
Unit_Diag_Bit(56) = "Sensor element exciter faulty"
Unit_Diag_Bit_Help(56) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(57) = "Error in evaluation electronics"
Unit_Diag_Bit_Help(57) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(58) = "Error in internal energy supply"
Unit_Diag_Bit_Help(58) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(59) = "Error in sensor element"
Unit_Diag_Bit_Help(59) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(60) = "Error in actuator element"
Unit_Diag_Bit_Help(60) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(61) = "Faulty installat e.g. dead space"
Unit_Diag_Bit_Help(61) = "Check installation."
Unit_Diag_Bit(62) = "Parameter setting error"
Unit_Diag_Bit_Help(62) = "Check parameter settings for consistency."
Unit_Diag_Bit(63) = "Signal path broken or short cut"
Unit_Diag_Bit_Help(63) = "Check signal path."
Unit_Diag_Bit(64) = "Overloading"
Unit_Diag_Bit_Help(64) = "Check load."
Unit_Diag_Bit(65) = "Wrong polarity of aux power"
Unit_Diag_Bit_Help(65) = "Check polarity."
Unit_Diag_Bit(66) = "Maximum line length exceeded"
Unit_Diag_Bit_Help(66) = "Check line length."
Unit_Diag_Bit(67) = "Corrosion/abrasion by medium"
Unit_Diag_Bit_Help(67) = "Replacement is recommended."
Unit_Diag_Bit(68) = "Fouling on sensor element"
Unit_Diag_Bit_Help(68) = "Cleaning is recommended."
Unit_Diag_Bit(69) = "Auxil medium missing or insuffic"
Unit_Diag_Bit_Help(69) = "Check auxiliary medium."
Unit_Diag_Bit(70) = "Wear reserve used up (operation)"
Unit_Diag_Bit_Help(70) = "Plan maintenance."
Unit_Diag_Bit(71) = "Wear reserve used up (wear)"
Unit_Diag_Bit_Help(71) = "Plan maintenance."
Unit_Diag_Bit(72) = "Error in peripherals"
Unit_Diag_Bit_Help(72) = "Check peripherals."
Unit_Diag_Bit(73) = "Electromag interference too high"
Unit_Diag_Bit_Help(73) = "Lower external electromagnetic interference."
Unit_Diag_Bit(74) = "Temperature of medium too high"
Unit_Diag_Bit_Help(74) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(75) = "Ambient temperature too high"
Unit_Diag_Bit_Help(75) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(76) = "Vibration/Impact load too high"
Unit_Diag_Bit_Help(76) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(77) = "Auxiliary power range off-spec"
Unit_Diag_Bit_Help(77) = "Check power supply"
Unit_Diag_Bit(78) = "Auxiliary medium missing"
Unit_Diag_Bit_Help(78) = "Check auxiliary medium."
Unit_Diag_Bit(79) = "Excessive temperature shock"
Unit_Diag_Bit_Help(79) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(80) = "Deviation from measurement"
Unit_Diag_Bit_Help(80) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(81) = "Humidity in electronics area"
Unit_Diag_Bit_Help(81) = "Replacement is recommended."
Unit_Diag_Bit(82) = "Medium in electronics area"
Unit_Diag_Bit_Help(82) = "Replacement is recommended."
Unit_Diag_Bit(83) = "Mechanical damage"
Unit_Diag_Bit_Help(83) = "Replacement is recommended."
Unit_Diag_Bit(84) = "Communication error"
Unit_Diag_Bit_Help(84) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(85) = "Foreign material in electro area"
Unit_Diag_Bit_Help(85) = "Replacement is recommended."
;NE107_ELECTRO_PNEUMATIC (device specific)
Unit_Diag_Bit(104) = "Minor drive leakage"
Unit_Diag_Bit_Help(104) = "1. Check air lines/connections. 2. Check actuator."
Unit_Diag_Bit(105) = "High friction"
Unit_Diag_Bit_Help(105) = "Check packing."
Unit_Diag_Bit(106) = "Feed air pressure off-spec"
Unit_Diag_Bit_Help(106) = "Check supply pressure."
Unit_Diag_Bit(107) = "Vent blockage"
Unit_Diag_Bit_Help(107) = "Check air lines/connections."
Unit_Diag_Bit(108) = "Diaphragm damage"
Unit_Diag_Bit_Help(108) = "Check pneumatic actuator."
Unit_Diag_Bit(109) = "Broken spring"
Unit_Diag_Bit_Help(109) = "Check pneumatic actuator."
Unit_Diag_Bit(110) = "Moist air in spring chamber"
Unit_Diag_Bit_Help(110) = "Check feed air."
Unit_Diag_Bit(111) = "Blocked drive"
Unit_Diag_Bit_Help(111) = "1. Check air supply. \
2. Check air lines/connections. 3. Check valve and attachment for wear."
Unit_Diag_Bit(112) = "Drive leakage too big"
Unit_Diag_Bit_Help(112) = "1. Check air lines/connections. \
2. Check pneumatic actuator."
Unit_Diag_Bit(113) = "Off-spec seat/plug leakage"
Unit_Diag_Bit_Help(113) = "Check seat/plug."
Unit_Diag_Bit(114) = "Off-spec spindle/shaft seal leak"
Unit_Diag_Bit_Help(114) = "Check stem/shaft."
Unit_Diag_Bit(115) = "Alteration and wear on spindle"
Unit_Diag_Bit_Help(115) = "Replace stem."
Unit_Diag_Bit(116) = "Altered friction"
Unit_Diag_Bit_Help(116) = "Check packing."
Unit_Diag_Bit(117) = "Wear in the valve"
Unit_Diag_Bit_Help(117) = "Replace valve."
Unit_Diag_Bit(118) = "Blocked valve"
Unit_Diag_Bit_Help(118) = "1. Check air supply. \
2. Check air lines/connections. 3. Check valve and attachment."
Unit_Diag_Bit(119) = "Change in valve move performance"
Unit_Diag_Bit_Help(119) = "1. Check air supply. 2. Check air \
lines/connections. 3. Check packing. 4. Check valve and attachment for wear."
Unit_Diag_Bit(120) = "Changed breakaway moment"
Unit_Diag_Bit_Help(120) = "1. Check packing. 2. Check seat/plug. \
3. Check attachment."
Unit_Diag_Bit(121) = "Spindle deformation"
Unit_Diag_Bit_Help(121) = "Replace stem."
Unit_Diag_Bit(122) = "Plug torn off"
Unit_Diag_Bit_Help(122) = "Replace plug."
Unit_Diag_Bit(123) = "Off-spec valve temperature"
Unit_Diag_Bit_Help(123) = "Check device/operating conditions."
Unit_Diag_Bit(124) = "Off-spec characteristic line"
Unit_Diag_Bit_Help(124) = "1. Check configuration. 2. Check sizing."
Unit_Diag_Bit(125) = "Fault in the pneumatic unit"
Unit_Diag_Bit_Help(125) = "Replace pneumatic unit."
Unit_Diag_Bit(126) = "Incorrect position sensing"
Unit_Diag_Bit_Help(126) = "1. Check travel sensor. 2. Check connections. \
3. Replace travel sensor or positioner."
Unit_Diag_Bit(127) = "Input signal off-spec"
Unit_Diag_Bit_Help(127) = "Check input signal."
Unit_Diag_Bit(128) = "Vibration off-spec"
Unit_Diag_Bit_Help(128) = "Check device/operating conditions."
Unit_Diag_Bit(129) = "Temp in positioner too high/low"
Unit_Diag_Bit_Help(129) = "Check device/operating conditions."
Unit_Diag_Bit(130) = "Moisture in positioner"
Unit_Diag_Bit_Help(130) = "Replace device. Check supply air."
Unit_Diag_Bit(131) = "Additional IO module defect"
Unit_Diag_Bit_Help(131) = "Replace module or device."
Unit_Diag_Bit(132) = "Signal without end position"
Unit_Diag_Bit_Help(132) = "Check limit switch."
Unit_Diag_Bit(133) = "No signal in end position"
Unit_Diag_Bit_Help(133) = "Check limit switch."
Unit_Diag_Bit(134) = "Control loop oscillation"
Unit_Diag_Bit_Help(134) = "1. Check control loop. 2. Check friction. \
3. Check supply pressure. 4. Check attachment."
Unit_Diag_Bit(135) = "Hysteresis"
Unit_Diag_Bit_Help(135) = "1. Check friction. 2. Check supply pressure."
Unit_Diag_Bit(136) = "Changed friction"
Unit_Diag_Bit_Help(136) = "Check packing."
Unit_Diag_Bit(137) = "Backlash between drive and valve"
Unit_Diag_Bit_Help(137) = "Check attachment."
Unit_Diag_Bit(138) = "Persistent deviation of control"
Unit_Diag_Bit_Help(138) = "1. Check attachment. 2. Check air supply. \
3. Check air lines/connections. 4. Check endpoint shift."
Unit_Diag_Bit(139) = "Inadmissible dynamic stress"
Unit_Diag_Bit_Help(139) = "1. Check operating conditions. 2. Check packing. \
3. Check sizing."
Unit_Diag_Bit(140) = "Faulty mounting"
Unit_Diag_Bit_Help(140) = "Check mounting."
Unit_Diag_Bit(141) = "Faulty mount positioner to drive"
Unit_Diag_Bit_Help(141) = "Check mounting."
Unit_Diag_Bit(142) = "Leak in piping"
Unit_Diag_Bit_Help(142) = "Check air lines/connections."
Unit_Diag_Bit(143) = "Insufficient drive power"
Unit_Diag_Bit_Help(143) = "1. Check air supply. 2. Check sizing."
Unit_Diag_Bit(144) = "Quality of feed air off-spec"
Unit_Diag_Bit_Help(144) = "Check quality of air supply."
Unit_Diag_Bit(145) = "Operator error during operation"
Unit_Diag_Bit_Help(145) = "Check configuration."
Unit_Diag_Bit(146) = "Inadmissible static stress"
Unit_Diag_Bit_Help(146) = "Check sizing."
Unit_Diag_Bit(147) = "Recording of pers. control dev."
Unit_Diag_Bit_Help(147) = "1. Check attachment. 2. Check air supply. \
3. Check air lines/connections."
Unit_Diag_Bit(148) = "Parameter plausibility check"
Unit_Diag_Bit_Help(148) = "Check configuration."
Unit_Diag_Bit(149) = "Status report on operating mode"
Unit_Diag_Bit_Help(149) = "Check mode."
Unit_Diag_Bit(150) = "Histogram for valve positions"
Unit_Diag_Bit_Help(150) = "1. Check attachment. 2. Check air supply. \
3. Check air lines/connections. 4. Check sizing."
Unit_Diag_Bit(151) = "Zero point and endpoint shift"
Unit_Diag_Bit_Help(151) = "Check the seat and plug."
Unit_Diag_Bit(152) = "Running time monitoring"
Unit_Diag_Bit_Help(152) = "Check the supply pressure and pneumatic connections."
Unit_Diag_Bit(153) = "Evaluation of internal signals"
Unit_Diag_Bit_Help(153) = "See detailed diagnostic information."
Unit_Diag_Bit(154) = "Operating hours counter"
Unit_Diag_Bit_Help(154) = "Check the valve and attachment for signs of wear."
Unit_Diag_Bit(155) = "Pressure-displacement diagram"
Unit_Diag_Bit_Help(155) = "1. Check attachment. 2. Check air supply. \
3. Check air lines/connections. 4. Check packing."
Unit_Diag_Bit(156) = "Total valve travel"
Unit_Diag_Bit_Help(156) = "Check the valve and attachment for signs of wear."
Unit_Diag_Bit(157) = "Step response diagnostics"
Unit_Diag_Bit_Help(157) = "See detailed test result."
Unit_Diag_Bit(158) = "Internal temperature monitoring"
Unit_Diag_Bit_Help(158) = "Check operating conditions."
Unit_Diag_Bit(159) = "Counter for direction changes"
Unit_Diag_Bit_Help(159) = "Check the valve and attachment for signs of wear."
Unit_Diag_Bit(160) = "Operating archive"
Unit_Diag_Bit_Help(160) = "See archive for detailed information."
Unit_Diag_Bit(161) = "Report archive"
Unit_Diag_Bit_Help(161) = "See archive for detailed information."
Unit_Diag_Bit(162) = "Status reports on access control"
Unit_Diag_Bit_Help(162) = "Check device configuration."
Unit_Diag_Bit(163) = "Cavitation / flashing"
Unit_Diag_Bit_Help(163) = "Check valve-operating conditions."
Unit_Diag_Bit(164) = "Partial stroke test"
Unit_Diag_Bit_Help(164) = "1. Check PST configuration. \
2. Check detailed test result."
Unit_Diag_Bit(165) = "P dif measurement across valve"
Unit_Diag_Bit_Help(165) = "Check friction."
Unit_Diag_Bit(166) = "Noise level measurement"
Unit_Diag_Bit_Help(166) = "Check the seat/plug for leakage."
;Unit_Diag_Bit(167) = ""
;Unit_Diag_Bit_Help(167) = ""
;---------------
UnitDiagType=254
X_Unit_Diag_Bit(35) = "Restart" ;DIA_WARMSTART
X_Unit_Diag_Bit(36) = "Application reset" ;DIA_COLDSTART
X_Unit_Diag_Bit(37) = "Maintenance required" ;DIA_MAINTENANCE
X_Unit_Diag_Bit(40) = "Maintenance alarm" ;DIA_MAINTENANCE_ALARM
X_Unit_Diag_Bit(41) = "Maintenance demanded" ;DIA_MAINTENANCE_DEMANDED
X_Unit_Diag_Bit(42) = "Function check" ;DIA_FUNCTION_CHECK
X_Unit_Diag_Bit(43) = "Out of specification" ;DIA_OUT_OF_SPEC
X_Unit_Diag_Bit(44) = "Parameter update" ;DIA_UPDATE_EVENT
X_Unit_Diag_Bit(55) = "Extension available"
;--- NE107_COMMON
X_Unit_Diag_Bit(56) = "Sensor element exciter faulty"
X_Unit_Diag_Bit_Help(56) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(57) = "Error in evaluation electronics"
X_Unit_Diag_Bit_Help(57) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(58) = "Error in internal energy supply"
X_Unit_Diag_Bit_Help(58) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(59) = "Error in sensor element"
X_Unit_Diag_Bit_Help(59) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(60) = "Error in actuator element"
X_Unit_Diag_Bit_Help(60) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(61) = "Faulty installat e.g. dead space"
X_Unit_Diag_Bit_Help(61) = "Check installation."
X_Unit_Diag_Bit(62) = "Parameter setting error"
X_Unit_Diag_Bit_Help(62) = "Check parameter settings for consistency."
X_Unit_Diag_Bit(63) = "Signal path broken or short cut"
X_Unit_Diag_Bit_Help(63) = "Check signal path."
X_Unit_Diag_Bit(64) = "Overloading"
X_Unit_Diag_Bit_Help(64) = "Check load."
X_Unit_Diag_Bit(65) = "Wrong polarity of aux power"
X_Unit_Diag_Bit_Help(65) = "Check polarity."
X_Unit_Diag_Bit(66) = "Maximum line length exceeded"
X_Unit_Diag_Bit_Help(66) = "Check line length."
X_Unit_Diag_Bit(67) = "Corrosion/abrasion by medium"
X_Unit_Diag_Bit_Help(67) = "Replacement is recommended."
X_Unit_Diag_Bit(68) = "Fouling on sensor element"
X_Unit_Diag_Bit_Help(68) = "Cleaning is recommended."
X_Unit_Diag_Bit(69) = "Auxil medium missing or insuffic"
X_Unit_Diag_Bit_Help(69) = "Check auxiliary medium."
X_Unit_Diag_Bit(70) = "Wear reserve used up (operation)"
X_Unit_Diag_Bit_Help(70) = "Plan maintenance."
X_Unit_Diag_Bit(71) = "Wear reserve used up (wear)"
X_Unit_Diag_Bit_Help(71) = "Plan maintenance."
X_Unit_Diag_Bit(72) = "Error in peripherals"
X_Unit_Diag_Bit_Help(72) = "Check peripherals."
X_Unit_Diag_Bit(73) = "Electromag interference too high"
X_Unit_Diag_Bit_Help(73) = "Lower external electromagnetic interference."
X_Unit_Diag_Bit(74) = "Temperature of medium too high"
X_Unit_Diag_Bit_Help(74) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(75) = "Ambient temperature too high"
X_Unit_Diag_Bit_Help(75) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(76) = "Vibration/Impact load too high"
X_Unit_Diag_Bit_Help(76) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(77) = "Auxiliary power range off-spec"
X_Unit_Diag_Bit_Help(77) = "Check power supply"
X_Unit_Diag_Bit(78) = "Auxiliary medium missing"
X_Unit_Diag_Bit_Help(78) = "Check auxiliary medium."
X_Unit_Diag_Bit(79) = "Excessive temperature shock"
X_Unit_Diag_Bit_Help(79) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(80) = "Deviation from measurement"
X_Unit_Diag_Bit_Help(80) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(81) = "Humidity in electronics area"
X_Unit_Diag_Bit_Help(81) = "Replacement is recommended."
X_Unit_Diag_Bit(82) = "Medium in electronics area"
X_Unit_Diag_Bit_Help(82) = "Replacement is recommended."
X_Unit_Diag_Bit(83) = "Mechanical damage"
X_Unit_Diag_Bit_Help(83) = "Replacement is recommended."
X_Unit_Diag_Bit(84) = "Communication error"
X_Unit_Diag_Bit_Help(84) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(85) = "Foreign material in electro area"
X_Unit_Diag_Bit_Help(85) = "Replacement is recommended."
;NE107_ELECTRO_PNEUMATIC (device specific)
X_Unit_Diag_Bit(104) = "Minor drive leakage"
X_Unit_Diag_Bit_Help(104) = "1. Check air lines/connections. \
2. Check actuator."
X_Unit_Diag_Bit(105) = "High friction"
X_Unit_Diag_Bit_Help(105) = "Check packing."
X_Unit_Diag_Bit(106) = "Feed air pressure off-spec"
X_Unit_Diag_Bit_Help(106) = "Check supply pressure."
X_Unit_Diag_Bit(107) = "Vent blockage"
X_Unit_Diag_Bit_Help(107) = "Check air lines/connections."
X_Unit_Diag_Bit(108) = "Diaphragm damage"
X_Unit_Diag_Bit_Help(108) = "Check pneumatic actuator."
X_Unit_Diag_Bit(109) = "Broken spring"
X_Unit_Diag_Bit_Help(109) = "Check pneumatic actuator."
X_Unit_Diag_Bit(110) = "Moist air in spring chamber"
X_Unit_Diag_Bit_Help(110) = "Check feed air."
X_Unit_Diag_Bit(111) = "Blocked drive"
X_Unit_Diag_Bit_Help(111) = "1. Check air supply. 2. Check air \
lines/connections. 3. Check valve and attachment for wear."
X_Unit_Diag_Bit(112) = "Drive leakage too big"
X_Unit_Diag_Bit_Help(112) = "1. Check air lines/connections. \
2. Check pneumatic actuator."
X_Unit_Diag_Bit(113) = "Off-spec seat/plug leakage"
X_Unit_Diag_Bit_Help(113) = "Check seat/plug."
X_Unit_Diag_Bit(114) = "Off-spec spindle/shaft seal leak"
X_Unit_Diag_Bit_Help(114) = "Check stem/shaft."
X_Unit_Diag_Bit(115) = "Alteration and wear on spindle"
X_Unit_Diag_Bit_Help(115) = "Replace stem."
X_Unit_Diag_Bit(116) = "Altered friction"
X_Unit_Diag_Bit_Help(116) = "Check packing."
X_Unit_Diag_Bit(117) = "Wear in the valve"
X_Unit_Diag_Bit_Help(117) = "Replace valve."
X_Unit_Diag_Bit(118) = "Blocked valve"
X_Unit_Diag_Bit_Help(118) = "1. Check air supply. \
2. Check air lines/connections. 3. Check valve and attachment."
X_Unit_Diag_Bit(119) = "Change in valve move performance"
X_Unit_Diag_Bit_Help(119) = "1. Check air supply. 2. Check air \
lines/connections. 3. Check packing. 4. Check valve and attachment for wear."
X_Unit_Diag_Bit(120) = "Changed breakaway moment"
X_Unit_Diag_Bit_Help(120) = "1. Check packing. 2. Check seat/plug. \
3. Check attachment."
X_Unit_Diag_Bit(121) = "Spindle deformation"
X_Unit_Diag_Bit_Help(121) = "Replace stem."
X_Unit_Diag_Bit(122) = "Plug torn off"
X_Unit_Diag_Bit_Help(122) = "Replace plug."
X_Unit_Diag_Bit(123) = "Off-spec valve temperature"
X_Unit_Diag_Bit_Help(123) = "Check device/operating conditions."
X_Unit_Diag_Bit(124) = "Off-spec characteristic line"
X_Unit_Diag_Bit_Help(124) = "1. Check configuration. 2. Check sizing."
X_Unit_Diag_Bit(125) = "Fault in the pneumatic unit"
X_Unit_Diag_Bit_Help(125) = "Replace pneumatic unit."
X_Unit_Diag_Bit(126) = "Incorrect position sensing"
X_Unit_Diag_Bit_Help(126) = "1. Check travel sensor. 2. Check connections. \
3. Replace travel sensor or positioner."
X_Unit_Diag_Bit(127) = "Input signal off-spec"
X_Unit_Diag_Bit_Help(127) = "Check input signal."
X_Unit_Diag_Bit(128) = "Vibration off-spec"
X_Unit_Diag_Bit_Help(128) = "Check device/operating conditions."
X_Unit_Diag_Bit(129) = "Temp in positioner too high/low"
X_Unit_Diag_Bit_Help(129) = "Check device/operating conditions."
X_Unit_Diag_Bit(130) = "Moisture in positioner"
X_Unit_Diag_Bit_Help(130) = "Replace device. Check supply air."
X_Unit_Diag_Bit(131) = "Additional IO module defect"
X_Unit_Diag_Bit_Help(131) = "Replace module or device."
X_Unit_Diag_Bit(132) = "Signal without end position"
X_Unit_Diag_Bit_Help(132) = "Check limit switch."
X_Unit_Diag_Bit(133) = "No signal in end position"
X_Unit_Diag_Bit_Help(133) = "Check limit switch."
X_Unit_Diag_Bit(134) = "Control loop oscillation"
X_Unit_Diag_Bit_Help(134) = "1. Check control loop. 2. Check friction. \
3. Check supply pressure. 4. Check attachment."
X_Unit_Diag_Bit(135) = "Hysteresis"
X_Unit_Diag_Bit_Help(135) = "1. Check friction. 2. Check supply pressure."
X_Unit_Diag_Bit(136) = "Changed friction"
X_Unit_Diag_Bit_Help(136) = "Check packing."
X_Unit_Diag_Bit(137) = "Backlash between drive and valve"
X_Unit_Diag_Bit_Help(137) = "Check attachment."
X_Unit_Diag_Bit(138) = "Persistent deviation of control"
X_Unit_Diag_Bit_Help(138) = "1. Check attachment. 2. Check air supply. \
3. Check air lines/connections. 4. Check endpoint shift."
X_Unit_Diag_Bit(139) = "Inadmissible dynamic stress"
X_Unit_Diag_Bit_Help(139) = "1. Check operating conditions. \
2. Check packing. 3. Check sizing."
X_Unit_Diag_Bit(140) = "Faulty mounting"
X_Unit_Diag_Bit_Help(140) = "Check mounting."
X_Unit_Diag_Bit(141) = "Faulty mount positioner to drive"
X_Unit_Diag_Bit_Help(141) = "Check mounting."
X_Unit_Diag_Bit(142) = "Leak in piping"
X_Unit_Diag_Bit_Help(142) = "Check air lines/connections."
X_Unit_Diag_Bit(143) = "Insufficient drive power"
X_Unit_Diag_Bit_Help(143) = "1. Check air supply. 2. Check sizing."
X_Unit_Diag_Bit(144) = "Quality of feed air off-spec"
X_Unit_Diag_Bit_Help(144) = "Check quality of air supply."
X_Unit_Diag_Bit(145) = "Operator error during operation"
X_Unit_Diag_Bit_Help(145) = "Check configuration."
X_Unit_Diag_Bit(146) = "Inadmissible static stress"
X_Unit_Diag_Bit_Help(146) = "Check sizing."
X_Unit_Diag_Bit(147) = "Recording of pers. control dev."
X_Unit_Diag_Bit_Help(147) = "1. Check attachment. 2. Check air supply. \
3. Check air lines/connections."
X_Unit_Diag_Bit(148) = "Parameter plausibility check"
X_Unit_Diag_Bit_Help(148) = "Check configuration."
X_Unit_Diag_Bit(149) = "Status report on operating mode"
X_Unit_Diag_Bit_Help(149) = "Check mode."
X_Unit_Diag_Bit(150) = "Histogram for valve positions"
X_Unit_Diag_Bit_Help(150) = "1. Check attachment. 2. Check air supply. \
3. Check air lines/connections. 4. Check sizing."
X_Unit_Diag_Bit(151) = "Zero point and endpoint shift"
X_Unit_Diag_Bit_Help(151) = "Check the seat and plug."
X_Unit_Diag_Bit(152) = "Running time monitoring"
X_Unit_Diag_Bit_Help(152) = "Check the supply pressure and pneumatic \
connections."
X_Unit_Diag_Bit(153) = "Evaluation of internal signals"
X_Unit_Diag_Bit_Help(153) = "See detailed diagnostic information."
X_Unit_Diag_Bit(154) = "Operating hours counter"
X_Unit_Diag_Bit_Help(154) = "Check the valve and attachment for signs of wear."
X_Unit_Diag_Bit(155) = "Pressure-displacement diagram"
X_Unit_Diag_Bit_Help(155) = "1. Check attachment. 2. Check air supply. \
3. Check air lines/connections. 4. Check packing."
X_Unit_Diag_Bit(156) = "Total valve travel"
X_Unit_Diag_Bit_Help(156) = "Check the valve and attachment for signs of wear."
X_Unit_Diag_Bit(157) = "Step response diagnostics"
X_Unit_Diag_Bit_Help(157) = "See detailed test result."
X_Unit_Diag_Bit(158) = "Internal temperature monitoring"
X_Unit_Diag_Bit_Help(158) = "Check operating conditions."
X_Unit_Diag_Bit(159) = "Counter for direction changes"
X_Unit_Diag_Bit_Help(159) = "Check the valve and attachment for signs of wear."
X_Unit_Diag_Bit(160) = "Operating archive"
X_Unit_Diag_Bit_Help(160) = "See archive for detailed information."
X_Unit_Diag_Bit(161) = "Report archive"
X_Unit_Diag_Bit_Help(161) = "See archive for detailed information."
X_Unit_Diag_Bit(162) = "Status reports on access control"
X_Unit_Diag_Bit_Help(162) = "Check device configuration."
X_Unit_Diag_Bit(163) = "Cavitation / flashing"
X_Unit_Diag_Bit_Help(163) = "Check valve-operating conditions."
X_Unit_Diag_Bit(164) = "Partial stroke test"
X_Unit_Diag_Bit_Help(164) = "1. Check PST configuration. \
2. Check detailed test result."
X_Unit_Diag_Bit(165) = "P dif measurement across valve"
X_Unit_Diag_Bit_Help(165) = "Check friction."
X_Unit_Diag_Bit(166) = "Noise level measurement"
X_Unit_Diag_Bit_Help(166) = "Check the seat/plug for leakage."
;X_Unit_Diag_Bit(167) = ""
;X_Unit_Diag_Bit_Help(167) = ""
EndUnitDiagType
;-------------------------------------------------------------------------
;
;max module text length-----------------"
Module="Not in cyclic data transfer " 0x00 ;Empty module
0
Info_Text="No cyclic data selected for this slot. Function disabled"
EndModule
Module="SP" 0x82, 0x84, 0x08, 0x05
1
EndModule
Module="SP, READBACK, POS_D" 0xC6,0x84,0x86,0x08,0x05,0x08,0x05,0x05,0x05
2
EndModule
Module="SP, CHECK_BACK" 0xC3,0x84,0x82,0x08,0x05,0x0A
3
EndModule
Module="SP, READBACK, POS_D, CHECK_BACK" 0xC7,0x84,0x89,0x08,0x05,0x08,0x05,\
0x05,0x05,0x0A
4
EndModule
;----------- Description of the module assignment: ---------------------
;
SlotDefinition
Slot(1) = "" 1 1-4
EndSlotDefinition